The HD range of HyDAF dissolved air flotation systems are designed for industrial applications where high solids loads are usually experienced. We have standard sizes that we manufacture but in each case we determine the most suitable model and dissolved air recycle system to suit the specific wastewater characteristics.
Dosing of chemicals into the wastewater upstream of the HyDAF dissolved air flotation system will improve the performance of the system. Whether it is necessary to dose chemicals depends on the water quality that is required. Hydroflux can tailor specific chemical programs to ensure performance requirements are met economically whilst minimising the amount of sludge that will be generated.
The amount of sludge generated depends on the amount of solids being removed and also whether chemicals are being dosed to enhance the performance of the HyDAF dissolved air flotation system. The dry solids concentration in the dissolved air flotation system sludge can be up to 10%. You can estimate the amount of sludge that will be generated by multiplying the solids load by the daily flow or alternatively give us a call and we will be able to assist. In larger applications the installation of a sludge dewatering plant will be highly economical.
The treated water quality depends on the nature of the raw wastewater and the chemical process that is applied. In many industrial applications, the HyDAF dissolved air flotation system can remove over 99% of solids and grease which will result in quite significant reductions in BOD and COD. Nutrients and metals can also be removed using the HyDAF dissolved air flotation process. .
Compared to the overall power requirements of a compelte wastewater treatment plant, the power demand for the actual HyDAF dissolved air flotation system is minimal. The dissolved air recycle pump draws the most power and is fitted with a motor ranging from 4 kW to 30kW depending on the size of the system.
It can but large solids can cause blockages and increase the chances of sedimentation occurring. In industrial applications we normally recommend the installation of a 1 -2 mm screen be installed upstream of the HyDAF dissolved air flotation system.
Yes the system can often be maintained by in-house personnel. Mechanically the HyDAF dissolved air flotation system rarely fails, the most common cause of poor performance is due to chemical programs malfunctioning which is usually due to changes in raw wastewater characteristics. Hydroflux can offer a service and preventative maintenance program if required.